5kVA single phase to split phase transformer can convert the primary voltage 230V into 120V/240V（L1, L2, N, L+L=240V, L+N=120V), enclosure protection grade IP20, the sturdy and durable structure makes it an ideal choice.
5 kVA Single Phase to Split Phase Transformer Specifications
||Single phase to split phase
||1 Phase / 2 phase 110, 120, 208, 220, 230, 240, 380, 415, 440, 460, 480,
||120V/240V AC（L1, L2, N, L+L=240V, L+N=120V）
||Aluminum/Copper wire (Optional)
||2000V AC/1 min
||≤35dB (1 meter)
||Grade B (130℃), Grade F (155℃), Grade H (180℃)
||Natural or air cooling
||Allow more than 1.2 times rated load to work for up to 1 hour
|Induced Overvoltage Withstand Test
|Air Carrying Current
||≤90%RH, without condensation
||<2000m, non corrosive gas and conductive dust
|Enclosure Protection Grade
|Weight of Aluminium Wire Transformer
||Open type: 65kg
Protected type: 84kg
|Weight of Copper Wire Transformer
||Open type: 75kg
Protected type: 100kg
5 kVA Single Phase to Split Phase Transformer Schematic Diagram
5 kVA Single Phase to Split Transformer Dimension (Unit: mm)
|Aluminium Wire Transformer Size
||Copper Wire Transformer Size
|Open type: a*b*c=290*300*350mm
||Open type: a*b*c=300*310*345mm
|Mouting size: D*E=150*180mm (aperture: 20*10mm)
||Mouting size: 190*190mm (aperture: 20*10mm)
|Protected type: A*B*C=380*530*560mm
||Protected type: A*B*C=380*530*560mm
Tips: How to adjust the transformer gear?
When adjusting the transformer gear, according to the output voltage level, adjust the tap switch to the corresponding position.
The steps to adjust the tap changer are:
1. Disconnect the transformer load, open the high-voltage drop-out fuse with an insulating rod, unscrew the protective cover of the transformer tap switch, and place the positioning pin in the neutral position.
2. When shifting gears, adjust the tap switch to the corresponding position according to the output voltage. When the voltage is too low, switch to the low-voltage gear, and when the voltage is too high, switch to the high-voltage gear.
3. After adjusting the gear, use a DC bridge to measure the DC resistance of each phase winding and check whether the DC resistance between the windings is balanced. If the phase-to-phase resistance difference is greater than 2%, it needs to be re-adjusted. Otherwise, the static and moving contacts will generate heat or even discharge due to poor contact and damage the transformer.