1-phase or 3-phase silent diesel generator 6kW 50Hz or 6.5kW 60Hz with powerful 10hp single cylinder air cooled diesel engine, 16L large fuel tank ensures hours of continuous running, CE, EPA aprroved, is usually used in places such as houses, shops without connection to a power grid, or as emergency power supply if the grid fails.
||Brushless, Self Exciting, 2 Pole, Single Phase (Three Phase generator is available)
- Single phase version: 110V, 120V, 220V, 230V, 240/110V, 120/240V, 208/120V
- Three phase version: 380/220V, 400/230V, 240/120V, 220/110V, 208/127V
*Note: For single phase version, voltage form like "240/110V" is a dual supply voltage, means that the generator output is 1-phase 240V or 1-phase 110V.
|Rated AC Output
|Max. AC Output
|DC Output Voltage
|DC Output Current
||Analog Panel (Option: Digital LCD Panel, ATS)
||Diesel, Air-cooled, Single Cylinder, 4-Stroke
|Bore x Stroke
|Starting Motor Capacity
|Max. Power Output
|Fuel Tank Capacity
|Operating Noise Level
||CE, EPA, ISO9001-2000
Output Socket Selection
Tips: Do not start the diesel generator with load
Before starting the diesel generator, pay attention to that the output air switch of the generator must be in the off state. After the start-up of the diesel engine of the common generator set, the temperature is low in winter after 3-5 minutes of idle operation (about 700 RPM), and the idle operation time should be appropriately extended for several minutes. After starting the diesel engine, first observe whether the oil pressure is normal and whether there is any abnormal phenomenon such as oil leakage and water leakage. (Under normal circumstances, the oil pressure must be above 0.2MPa). In case of any abnormality, stop the engine immediately for maintenance.
If there is no abnormal phenomenon, the diesel engine speed will be increased to the rated speed of 1500 rpm, at this time, the generator display frequency is 50Hz and the voltage is 400V, then the output air switch can be closed and put into use. The generator set is not allowed to operate without load for a long time. (Because long-term no-load operation will make the diesel fuel injected from the diesel engine injector not completely burn, resulting in carbon deposition, resulting in air leakage of valves and piston rings.) If it is an automatic generator set, it does not need to run at idle speed, because the automatic generator set is generally equipped with a water heater, so that the diesel engine cylinder body is always kept at about 45 ℃, and the power can be normally delivered within 8-15 seconds after the diesel engine is started.