High quality and safety isolating transformers, 3 phase, 20kVA power rating, 380V AC input voltage to 190V AC output voltage, is a is a non-ventilated isolation transformer rated for hazardous locations as well as harsh industrial environments.
20 kVA Isolation Transformer Specifications
|Weight of Aluminium Wire Transformer
||Open type: 110kg
Protected type: 135kg
|Weight of Copper Wire Transformer
||Open type: 120kg
Protected type: 145kg
||380V (Optional: 120V/ 190V/ 208V/ 220V/ 230V/ 240V/ 380V/ 400V/ 415V/ 480V)
||190V (Optional: 120V/ 190V/ 208V/ 220V/ 230V/ 240V/ 380V/ 400V/ 415V/ 480V)
||Three phase to three phase
||50Hz / 60 Hz
||Aluminium/Copper wire (Optional)
||3000V AC/1 min
||<35-65dB (1 meter)
||Dry type air cooling
||Allow more than 1.2 times rated load to work for up to 4 hours
|Enclosure Protection Grade
||≤90%RH, without condensation
||<1000m, non corrosive gas and conductive dust
Transformer can only convert voltage and CANNOT convert frequency.
Transformer CANNOT convert single phase voltage to 3 phase voltage.
Input/output voltage, power rating and whether with shell of all transformers, can be customized according to clients' requirements.
3 Phase Isolation Transformer Schematic Diagram
20 kVA Isolation Transformer Installation Dimension
|Aluminium Wire Transformer Size
||Copper Wire Transformer Size
|Open type: a*b*c=440*310*430mm
||Open type: a*b*c=440*310*420mm
|Protected type: A*B*C=610*420*610mm
||Protected type: A*B*C=610*420*610mm
|Installation Dimenion: D*E=300*165mm
||Installation Dimenion: D*E=300*165mm
Tips: 3 phase isolation transformer loss
When the 3 phase isolation transformer output power is equal to the input power, the efficiency reaches 100%, the transformer will not generate any loss. But in fact this kind of transformer does not exist. Transformer always generates loss during electricity transmission, this kind of loss mainly includes copper loss and iron loss. Copper loss refers to the loss caused by step up & step down transformer coil resistance. When the current goes through the coil resistance and gets heated, part of the electrical energy is consumed and becomes heat loss. Since the coil is generally twined with insulated copper wire, it is called copper loss.
Iron loss of the transformer includes two aspects. The first one is the hysteresis loss, when the alternating current goes through the transformer, the direction and magnitude of the magnetic lines through the transformer silicon steel sheet changes, causing friction among the molecules within the silicon steel sheet and heat is released, this process consumes part of the electricity. The other is eddy current loss during the working of isolation transformer. When the magnetic line of force goes through iron core, current will be induced on the plane vertical to the magnetic line of force, since the current forms a closed loop and becomes ring current which shapes an eddy, it is called eddy current. The existence of eddy current makes the core heat and consumes energy, this loss is called eddy current loss.