Cheap 50 kVA isolation transformer is available in the circuit of AC 50Hz/ 60Hz, it can step down 3 phase voltage 480V to 400V, step up 400V to 480V transformer is available, suitable for indoor applications.
50 kVA Isolation Transformer Specifications
|Weight of Aluminium Wire Transformer
||Open type: 225kg
Protected type: 280kg
|Weight of Copper Wire Transformer
||Open type: 230kg
Protected type: 265kg
||480V (Optional: 120V/ 190V/ 208V/ 220V/ 230V/ 240V/ 380V/ 400V/ 415V/ 480V)
||400V (Optional: 120V/ 190V/ 208V/ 220V/ 230V/ 240V/ 380V/ 400V/ 415V/ 480V)
||Three phase to three phase
||50Hz / 60 Hz
||Aluminium/Copper wire (Optional)
||3000V AC/1 min
||<35-65dB (1 meter)
||Dry type air cooling
||Allow more than 1.2 times rated load to work for up to 4 hours
|Enclosure Protection Grade
||≤90%RH, without condensation
||<1000m, non corrosive gas and conductive dust
Transformer can only convert voltage and CANNOT convert frequency.
Transformer CANNOT convert single phase voltage to 3 phase voltage.
Input/output voltage, power rating and whether with shell of all transformers, can be customized according to clients' requirements.
3 Phase Isolation Transformer Schematic Diagram
50 kVA Isolation Transformer Installation Dimension
|Aluminium Wire Transformer Size
||Copper Wire Transformer Size
|Open type: a*b*c=560*330*550mm
||Open type: a*b*c=500*350*470mm
|Mouting size: d*e=380*190mm
||Mouting size: d*e=340*205mm
|Protected type: A*B*C=550*950*930mm
||Protected type: A*B*C=455*660*710mm
Tips: How the noise of 3 phase isolation transformer is caused
Specifically, there are three noise sources in the 3 phase isolation transformer including iron core, winding and cooler, which is the noise of no-load, load and cooling system. The reason of the iron core noise is that under the action of the iron core silicon steel sheet alternating magnetic field, slight change which is magnetostriction occurs. Magnetostriction causes the iron core to periodically vibrate with changes of the excitation frequency, which is caused by magnetostrictive deformation of the iron core, windings, oil tank and electromagnetic force within the magnetic shield. The reason for the vibration of the winding is that electromagnetic force is generated in the current winding, the leakage magnetic field can also make the structure vibrate.
The reason of the electromagnetic noise is that the magnetic field induces the vibration of the iron core lamination along the longitudinal direction to generate noise, the vibration amplitude is related to the magnetic flux density of the core lamination and the magnetic properties of the iron core material, it has little relation with the load current. The electromagnetic force (and vibration amplitude) is proportional to the square of the current, and the emitted sound power is proportional to the square of the vibration amplitude.