1000VA/600 Watts UPS is an uninterruptible power source and mainly used in computer, office equipment, test equipment, light system, safe alarm system, ray equipment, medical equipment, copymachine, numerical control machine tools, industrial automation equipment, color and drying equipment, Hi-Fi equipment etc.
600W UPS Specification
||Input Voltage Range
|Nominal Input Voltage
||Norminal Output Voltage
|Output Voltage Range (Normal Mode)
|Output Voltage Range (Battery Mode)
||220/230/240/110/120V AC±10% (Modified Sine Wave)
|Output Frequency (Normal Mode)
||Synchronized (Sine Wave)
|Output Frequency (Battery Mode)
||Modified Sine Wave
|Batteries & Runtime
||Maintenance-free lead-acid battery
|Backup Time (full/half load)
||5 Minutes Backup time; for long backup mode, it depends on outside battery
||<12 hours (90%)
||LCD (NORMAL, FAULT, BATTERY, CHARGE, OVERLOAD)
||Automatic shut down when overload is within 110~130% after 10 seconds
|Shut down after 300ms when above 130%
||Peak Ratio for Load
|Distortion Rate (full load) Linear Load
|Distortion Rate (full load) Non-linear Load
UPS Input Power Cables (Optional)
UPS Output Sockets (Optional)
Tips: Composition of UPS power supply
UPS power supply consists of five parts, main circuit, bypass circuit, battery and other power input circuits, AC/DC converter rectifier (REC), DC/AC transform inverter (INV), inverter and bypass output switching circuit, and battery.
The voltage stabilization function of UPS system is usually done by the rectifier. The rectifier adopts silicon control or high-frequency switch rectifier. It has the function of controlling output amplitude according to the change of external electricity, so that when external electricity changes (this change should meet the requirement of the system), the voltage with output amplitude is basically unchanged.
The purification function is completed by the energy storage battery. Because the rectifier’s interference on instantaneous impulse cannot be eliminated, there still exists interfering impulse of the voltage after rectification. In addition to the function of direct-current and direct energy storing, the storing battery is just as if to be connected by a large container capacitor for the rectifier. The size of the equivalent capacitance is in proportion to the capacity of energy storage battery. Because the voltage at both ends of capacitor is not mutable, it means that it plays the role of purification (also called the shielding of interference) by the smoothness properties of the capacitor on the pulse to eliminate the impulse interference.
The stabilization of frequency is accomplished by the converter and the frequency stability depends on stability degree of converter oscillation frequency.