2000VA/1600W UPS is an backup power supply to provide emergency power to a load, and it is mainly used in computer, office equipment, test equipment, light system, safe alarm system, ray equipment, medical equipment, copymachine, numerical control machine tools, industrial automation equipment, color and drying equipment, Hi-Fi equipment etc.
2kVA/1600W UPS Specification
||Single Phase (L, N, G)
||Input Voltage Range
||172-275V AC/ 85-135V AC
|Nominal Input Voltage
||Norminal Output Voltage
|Output Voltage Range (Normal Mode)
|Output Voltage Range (Battery Mode)
||220V/120V AC±10% (Modified Sine Wave)
|Output Frequency (Normal Mode)
||Synchronized (Sine Wave)
|Output Frequency (Battery Mode)
||Modified Sine Wave
|Batteries & Runtime
||Maintenance-free lead-acid battery
|Backup Time (full/half load)
||5 Minutes Backup time; for long backup mode, it depends on outside battery
||<12 hours (90%)
||LCD (NORMAL, FAULT, BATTERY, CHARGE, OVERLOAD)
||Automatic shut down when overload is within 110~130%
|Shut down after 300ms when above 130%
||Peak Ratio for Load
|Distortion Rate (full load) Linear Load
|Distortion Rate (full load) Non-linear Load
1. The UPS input/output configuration is 1-phase (L, N, G) like Europe standard, NOT support the split phase (L1, L2 + G) like USA standard.
2. If you need other output voltage range, please contact us.
Tips: Why we need a UPS (Uninterruptible Power Supply) for computer?
There are at least nine problems in the power grid, interruption of power supply, lightning stroke spike, surge, frequency oscillation, voltage mutation, voltage fluctuation, frequency drift, voltage drop and pulse interference. Therefore, it is necessary to equip a computer with an uninterruptible power supply (UPS) from the perspective of improving the power quality.
In addition, the power supply is not allowed to be interrupted in precise network equipment and communication equipment. It is self-evident to equip UPS battery backup to the network center with the core of server. Even if it is an ordinary computer, its data file and other software value exceeds the hardware value after being used for three months. Therefore, it is really necessary to equip uninterruptible power supply (UPS) to prevent the data loss.