5kVA/4000 Watts UPS battery backup provides uninterruptible power source for the loaded equipment or devices with optional input and output voltages of 220V/230V/240V/110V/120V AC, and the reliable UPS is widely applied for personal computer, office equipment, test equipment, light system, safe alarm system, ray equipment, medical equipment, copymachine, numerical control machine tools, industrial automation equipment, color and drying equipment, Hi-Fi equipment etc.
5kVA UPS Specification
||Single Phase (L, N, G)
||Input Voltage Range
|Nominal Input Voltage
||Norminal Output Voltage
|Output Voltage Range (Normal Mode)
|Output Voltage Range (Battery Mode)
||220V/230V/240V/110V/120V AC±10% (Modified Sine Wave)
|Output Frequency (Normal Mode)
||Synchronized (Sine Wave)
|Output Frequency (Battery Mode)
||Modified Sine Wave
|Batteries & Runtime
||Maintenance-free lead-acid battery
|Backup Time (full/half load)
||5 Minutes Backup time; for long backup mode, it depends on outside battery
|Typical Charge Time
||<12 hours (90%)
||LCD (NORMAL, FAULT, BATTERY, CHARGE, OVERLOAD)
||Automatic shut down when overload is within 110~130%
|Shut down after 300ms when above 130%
||Peak Ratio for Load
|Distortion Rate (full load) Linear Load
|Distortion Rate (full load) Non-linear Load
Note: The UPS input/output configuration is 1-phase (L, N, G) like Europe standard, NOT support the split phase (L1, L2 + G) like USA standard.
UPS Input Power Cables (Optional)
UPS Output Sockets (Optional)
Tips: Maintenance of uninterruptible power supply (UPS)
1. Maintain the appropriate ambient temperature
The important factors affecting the life service of battery is ambient temperature. Although the increase in temperature increases the discharge capacity of the battery, the life service of the battery is greatly shortened.
2. Regular charging and discharging
The battery will remain in the floating charge environment for a long time if it is in the use environment of high electric quality and few power failures, thus causing the decrease of the activity of mutual transformation of battery chemical energy and electric energy, acceleration of its aging and shortening of its life service. Therefore, it should be discharged completely every 2-3 months. The discharging time depends on the battery capacity and the load. After the discharging of a full load, the battery should be charged for at 8 hours as provided.
3. Communication function
Most large and medium UPS have operational performance with microcomputer communication and program control.The corresponding software is installed on the microcomputer, which is connected to UPS by series or parallel port. You can use microcomputer to communicate with UPS during the operation of this procedure.Generally, it has the functions of information inquiry, parameter setting, timing setting, automatic shutdown and alarm. It is convenient for the use management of UPS power and battery through these intelligent operations.
4. Timely replacement of waste or bad battery
In the continuous operation of UPS, due to the difference in performance and quality, it is inevitable that the performance of individual batteries will decline, and the storage capacity will not meet the requirements.When a battery or some batteries are damaged in the battery pack, the maintenance staff should check and test each battery to remove the damaged battery. The same type battery of the same manufacturer should be replaced. The acid battery, sealing the battery, or batteries of different specifications are not allowed to be used together.