4000VA/3200 Watts uninterruptible power supply provides UPS battery backup for the loaded equipment or devices with input and output voltages of 220V/120V AC, such as computer, office equipment, test equipment, light system, safe alarm system, ray equipment, medical equipment, copymachine, numerical control machine tools, industrial automation equipment, color and drying equipment, Hi-Fi equipment etc.
4kVA UPS Specification
||Single Phase (L, N, G)
||Input Voltage Range
||172-275V AC/ 85-135V AC
|Nominal Input Voltage
||Norminal Output Voltage
|Output Voltage Range (Normal Mode)
|Output Voltage Range (Battery Mode)
||220V/120V AC±10% (Modified Sine Wave)
|Output Frequency (Normal Mode)
||Synchronized (Sine Wave)
|Output Frequency (Battery Mode)
||Modified Sine Wave
|Batteries & Runtime
||Maintenance-free lead-acid battery
|Backup Time (full/half load)
||5 Minutes Backup time; for long backup mode, it depends on outside battery
|Typical Charge Time
||<12 hours (90%)
||LCD (NORMAL, FAULT, BATTERY, CHARGE, OVERLOAD)
||Automatic shut down when overload is within 110~130%
|Shut down after 300ms when above 130%
||Peak Ratio for Load
|Distortion Rate (full load) Linear Load
|Distortion Rate (full load) Non-linear Load
1. The UPS input/output configuration is 1-phase (L, N, G) like Europe standard, NOT support the split phase (L1, L2 + G) like USA standard.
2. If you need other output voltage range, please contact us.
Tips: How to prolong the power-on time of UPS power supply?
There are two ways to prolong the power-on time of UPS system.
1. External connection of high-capacity battery group to UPS
The corresponding capacity battery backup shall be connected according to the power-on time required. But it should be noted that this kind of method will increase the charging period of the battery pack, floor area and maintenance cost.
2. Choose high-capacity UPS system
This method can not only reduce the cost of maintenance. If the load equipment is expanded, the high capacity UPS system can still operate immediately.