ATO-DG20KVA single phase isolation transformer is 20 kVA capacity, applies to AC 50/ 60Hz, convert 240V voltage to 208V voltage. It has natural air self cooling mode, primary and secondary windings are separated by aluminum shield, long life span and high efficiency.
20 kVA Isolation Transformer Specifications
||240V AC (optional: 110V/ 120V/ 208V/ 220V/ 230V)
||208V AC (optional: 110V/ 120V/ 220V/ 230V/ 240V)
||50Hz / 60Hz
||Aluminum/Copper wire (Optional)
||2000V AC/1 min
||≤35dB (1 meter)
||Grade B (130℃), Grade F (155℃), Grade H (180℃)
||Natural or air cooling
||Allow more than 1.2 times rated load to work for up to 1 hour
|Induced Overvoltage Withstand Test
|Air Carrying Current
||≤90%RH, without condensation
||<2000m, non corrosive gas and conductive dust
|Enclosure Protection Grade
|Weight of Aluminium Wire Transformer
||Open type: 92kg
Protected type: 120kg
|Weight of Copper Wire Transformer
||Open type: 115kg
Protected type: 141kg
Transformer can only convert voltage and CANNOT convert frequency.
Transformer CANNOT convert single phase voltage to 3 phase voltage.
Support voltage customization, various specifications customization.
Single Phase Isolation Transformer Schematic Diagram
20 kVA Isolation Transformer Dimension
|Aluminium Wire Transformer Size
||Copper Wire Transformer Size
|Open type: a*b*c=330*300*470mm
||Open type: a*b*c=300*370*345mm
|Mouting size: D*E=170*160mm (aperture: 20*10mm)
||Mouting size: D*E=210*190mm (aperture: 20*10mm)
|Protected type: A*B*C=420*610*610mm
||Protected type: A*B*C=420*610*610mm
Tips: What are the differences among a transformer, a voltage stabilizer and a voltage regulator?
A transformer can control the unstable voltage in a certain voltage range and protect the equipment from being damaged. A voltage regulator converts a specific voltage to the needed voltage of an equipment, each equipment should be equipped with a voltage regulator to prevent from burning out equipment caused by excessive voltage change. A voltage stabilizer is used to stabilize the voltage. Generally, a voltage regulator is a kind of test equipment that can change the voltage, while a voltage stabilizer can only adjust the voltage in a certain range. The voltage regulator can adjust the high voltage, but can’t insulate it, while the transformer is generally used to isolate, such as the isolation transformer, the transformer can be used to step up or step down the voltage. A voltage stabilizer is just a way to stabilize the voltage.