The product has one normal open contact, has been designed for direct current loads, particularly for electric vehicle, telecommunication equiment, car batteries, trains, ships, electronic control system.
50A DC Contactor Features
- 50 amps rated load current of contact circuit.
- 12V, 24V, 48V DC coil rated voltage for selection.
- Continuous operation duty.
- Easy and quick installation, available any way to install.
- Mechanical life up to 300 thousand times.
||Coil Rated Voltage
|Contact Circuit Rated Load Current
|Main contact voltage drop at 100A
|The Allowed Range of Coil Voltage
|Pull-In Time (N/O Contacts to Open)
|Drop-Out Time (N/O Contact to Close)
|Dielectric Withstanding Voltage
||Continuous 30000 times
||300 thousand times
ATO-AZJ50 DC Contactor Circuit Diagram
50A DC Contactor Installation Diagram
Tips: Different Functions between contactor and relay
Primary function of a relay is to detect, transmit, convert or dispose the signal, it's on-off current is generally small. The relay is usually used in a control circuit to control the weak signal.
Primary function of a contactor is to connect or disconnect the main circuit. The main circuit refers to the one whose working situation is determined by the connection of this circuit. The concept of main circuit corresponds to the control circuit, generally, the current of a main circuit is larger than that of a control circuit.
In general, a contactor with large capacity is equipped with an arc chute. The contact capacity of a relay will not exceed 5A, that of a midget relay may be 1A or 2A. However, the minimum contact capacity of a contactor could be 9A. Contacts of the contactor usually have three pairs of main contacts (the main contacts are normally open contacts), it also has several pairs of auxiliary contacts.
However, contacts of a relay is generally not divided into main contacts or auxiliary contacts. Sometimes, contacts of a relay are set in pairs, namely the normally open contacts and normally closed contacts are combined, while that of a contactor are not in pairs. As for specific needs, the relay will combine with other equipment into a time relay, a counter or a pressure relay, which has the additional functions, but a contactor doesn't have.