3 pole 10 hp(7.5 kW) with work frequency 50/60Hz, work voltage with 220V, 380V, 400V, 410V, 440V, 460V or 480V for selection, rated current 10A, for vfd. Excellent quality and reasonable price, you deserve it.
3-Phase Line output Reactor Specifications
||10 hp (7.5 kW)
||Class F, H
||380V (optional: 220V/ 240V/ 400V/ 415V/ 440V/ 460V/ 480V)
||Copper or Aluminum
||≤4﹪higher than the range will cause the loss of torque
||1.5 times rated the current continues 60s
|Running Ambient Temperature
||≤90%RH, without condensation
3-Phase Output Line Reactor Mounting Dimension
3-Phase Output Line Reactor Circuit Diagram
Tips: How to Maintain Line Reactor?
Prevention of oil leakage: the oil tank of oil-immersed line reactor is filled with line reactor oil and oil-immersed line reactor is sealed with grease-proof rubber elements pressed by fastener in assembly. Poor sealing is the main cause for oil leakage of Line reactor, so user should pay attention it in maintenance.
Wetting prevention of line reactor: as a high voltage equipment, line reactor should have a good insulation. Oil-immersed type reactor is easy to be wetted, so wetting prevention is one of the main measures in maintenance of line reactor.
Oil replacement and drying treatment of line reactor: if the long idle time or operation time or other nature and human factors cause insulation deterioration of line reactor, water inflow or oil deterioration, oil replacement and drying treatment should be conducted to line reactor. Of line reactor: lift the body of line reactor out, drain sump oil, wash oil tank, and wash the greasy dirt on the body of line reactor if any. After drying, fill line reactor with oil and replace all grease-proof rubber seals The line reactor can be operated only after passing the test.