Digital timer relays, 8-pin time delay relay, have timing setting range 0.01~999s/0.01~999min/0.01~999h, easy to read with 3-digit display. High quality and low price digital timer relay is widely applied in the industrial automation field with operating voltage 12V DC, 24V DC or 220V AC.
Digital Timer Relay Specification
|Mode of Operation
||On delay timer
|Supply Voltage (Optional)
||220V AC or 12V DC or 24V DC
|Output Mode (Optional)
||Mode 2: One group instantaneous and one group delay output
Mode 3: One group suspension delay output
Mode 4: Two groups sync delay output
|Time Setting Range
||3A 250V AC (Resistive Load)
||8-pin Mounting Socket
||-10 ~ 50℃
||≤85% no caustic or magnetic interference
Digital Timer Dimensions (Unit: mm)
• ATO-TH200 Digital Timer Relay Dimension • ATO-TH300 Digital Timer Relay Dimension
Digital Timer Relay Connections & Output Operation Modes
• Mode 2: One group of contacts instantaneous and one group time limit output • Mode 3: One group of contacts time limit output
• Mode 4: Two groups of contacts sync time limit output
Tips: How a time delay relay work?
Timer relay or time delay relay is a kind of relay that realized the time delay control based on the electromagnetic principle or mechanical principle.
When the coil is energized, the armature and the pallet are attracted by the iron core and move down instantaneously, so that the instantaneous group of contact is switched on or off. But the piston rod and the lever cannot fall along with the armature at the same time. The upper end of the piston rod is connected to the rubber film in the air chamber. When the piston rod starts to move down under the action of releasing the spring, the rubber film is then concave down, and the air in the above chamber becomes thin to make the piston rod fall slowly affected by damping. After a certain period of time, the piston rod moves down to a certain position, and the delay time contact is actuated by the lever, so that the normally closed contact is open and the normally open contact is closed. From the powering-on of the coil to the completion of the delay time contact action, this period is the time limit of the timer relay. The length of the delay time can be changed by adjusting the size of the air inlet of the air chamber. After the coil is de-energized, the relay relies on the recovery spring to restore.