The 5kVA isolation transformer is high quality, three phase, 480V primary voltage and 400V secondary voltage, manufactured direct sale. Fully compliant with reduced low voltage regulations, is a non-ventilated isolation transformer rated for hazardous locations as well as harsh industrial environments.
5 kVA Isolation Transformer Specifications
|Weight of Aluminium Wire Transformer
||Open type: 55kg
Protected type: 70kg
|Weight of Copper Wire Transformer
||Open type: 60kg
Protected type: 80kg
||480V (Optional: 120V/ 190V/ 208V/ 220V/ 230V/ 240V/ 380V/ 400V/ 415V/ 480V)
||400V (Optional: 120V/ 190V/ 208V/ 220V/ 230V/ 240V/ 380V/ 400V/ 415V/ 480V)
||50Hz / 60 Hz
||Aluminium/Copper wire (Optional)
||3000V AC/1 min
||<35-65dB (1 meter)
||Dry type air cooling
||Allow more than 1.2 times rated load to work for up to 4 hours
|Enclosure Protection Grade
||≤90%RH, without condensation
||<1000m, non corrosive gas and conductive dust
*Transformer can only convert voltage and CANNOT convert frequency.
*Transformer CANNOT convert single phase voltage to 3 phase voltage.
*Input/output voltage, power rating and whether with shell of all transformers, can be customized according to clients' requirements.
3 Phase Isolation Transformer Schematic Diagram
3 Phase Isolation Transformer Details
5 kVA Isolation Transformer Installation Dimension
|Aluminium Wire Transformer Size
||Copper Wire Transformer Size
|Open type: a*b*c=380*200*380mm
||Open type: a*b*c=300*170*310mm
|Mouting size: d*e=260*110mm
||Mouting size: d*e=180*140mm
|Protected type: A*B*C=300*440*500mm
||Protected type: A*B*C=300*440*500mm
Tips: Dyn11 Wiring Method of 3 Phase Step up & Step down Isolation Transformer
Dyn11 is ATO step up/down isolation transformers wiring method. D represents that the primary winding adopts triangular form wiring, Y represents the secondary measuring winding adopts star form wiring, n represents to lead the neutral line, 11 represents that the secondary winding phase angle lags 330 degrees compared with the first winding. If use clock representation method and assume the primary winding locates at the center of 12 o'clock, then the secondary winding locates at 11 o'clock position with an included angle of 30 degrees.