10 HP portable water chiller machine for sales, 8 ton refrigerating capacity, works in three phase four wire 50Hz or 60Hz power supply, 240V/ 400V/ 480V AC voltage are optional. It is widely used in industrial injection molding machine, film blowing machine, laser cutting, chemical and pharmaceutical fields etc..
- Adopted high quality compressors and pumps to ensure safe & quiet running, power saving and durable service life.
- Employed microcomputer with easy operation which can control temperature within 3℃ to 45℃ precisely.
- Unique design for condenser and heat-dispersion unit result in excellent heat-exchange effect.
- Equiped with electrical current overload protection, high & low pressure switch, electrical timer delay safety device. It will alarm to display faulty while any malfunction occurs.
- Built in stainless steel insulated water tank, durable and easy to clean.
- Complete safely devices including power reverse phase, power short phase and anti-freeze protection.
- Ultra low temperature type of chiller can reach below -60℃.
|Number of Compressors
|Compressor Total Power
||R22 / R407C (Optional)
||Spiral type / Tube-in-shell type (Optional)
|Number of Fan
|Single Fan power
|Number of Cooling Water Inlet/Outlet
|Cooling Water Inlet/Outlet Size
|Water Tank Capacity
||3-phase 4-wire AC 208V/60Hz, 220V/60Hz, 240V/60Hz, 380V/50Hz, 400V/50Hz, 415V/50Hz, 480V/60Hz (Optional)
||1-phase AC 220V (L+N)
1. The "cooling capacity" is tested based on: Inlet and outlet water temperature of freezing is 12℃/7℃, and the inlet and outlet water temperature of cooling is 30℃/35℃.
2. Working temperature range: Chilled water temperature range is 5℃-35℃, inlet and outlet water temperature difference is 3℃-8℃, condensation temperature not higher than 35℃.
3. Conversion of units: 1 ton cooling capacity=3024kcal/hr, 1kcal/hr=3.969BTU/hr, 1HP=0.735kW=2580kcal/hr
Water Chiller Structure Diagram
||High pressure gauge
||Low pressure gauge
Tips: Can industrial water chiller be cleaned with acid?
In normal applications, chiller requires regular and scientific cleaning, which is also an indispensable part of maintenance. Mainly condensers, evaporators, various pipes, etc., especially the condensers and evaporators of water-cooled type chiller, must be regularly cleaned.
Pickling can be applied as a cleaning method. However, the degree of dilution of the acid solution and the type of acid solution need to be considered. Basically, almost all condensers can be cleaned using acid. In addition, it is necessary to consider whether the components of the water chiller to be cleaned are a certain part or the entire cycle operation system. These two aspects are completely different.
In case of cleaning the circulating operation system, it is necessary to ensure that the system is completely closed, and connect the cleaning pump, liquid distribution tank and relevant valves of the refrigerator. If it is cleaned separately, it is necessary to remove the condenser, and then add the diluted acid into it. It must be filled to achieve the corresponding cleaning effect. The reason why it is necessary to clean the chiller is that there are many parts in the chiller that will affect the normal operation of the whole water chiller.