80 kVA isolation transformer is designed to step down/up the 3 phase voltage 480V to 380V, and widely used in various power supply sites with frequency 50Hz/60Hz. It is designed for use in control circuits and general applications such as mechanical and electronic equipment, precision machine tool, CNC machine tool, lighting, etc.
80 kVA Isolation Transformer Specifications
|Weight of Aluminium Wire Transformer
||Open type: 320kg
Protected type: 385kg
|Weight of Copper Wire Transformer
||Open type: 325kg
Protected type: 395kg
||480V (Optional: 190V/ 208V/ 220V/ 230V/ 240V/ 380V/ 400V/ 415V/ 480V)
||380V (Optional: 190V/ 208V/ 220V/ 230V/ 240V/ 380V/ 400V/ 415V/ 480V)
||Three phase to three phase
||50Hz / 60 Hz
||Aluminium/Copper wire (Optional)
||3000V AC/1 min
||<35-65dB (1 meter)
||Dry type air cooling
||Allow more than 1.2 times rated load to work for up to 4 hours
|Enclosure Protection Grade
||≤90%RH, without condensation
||<1000m, non corrosive gas and conductive dust
Transformer can only convert voltage and CANNOT convert frequency.
Transformer CANNOT convert single phase voltage to 3 phase voltage.
Input/output voltage, power rating and whether with shell of all transformers, can be customized according to clients' requirements.
3 Phase Isolation Transformer Schematic Diagram
3 Phase Isolation Transformer Details
80 kVA Isolation Transformer Installation Dimension
|Aluminium Wire Transformer Size
||Copper Wire Transformer Size
|Open type: a*b*c=760*370*600mm
||Open type: a*b*c=560*380*530mm
|Mouting size: d*e=420*220mm
||Mouting size: d*e=380*230mm
|Protected type: A*B*C=600*1050*980mm
||Protected type: A*B*C=600*1050*980mm
Tips: Application of burglar alarm in isolation transformer
Since outdoor transformer is often stolen, the product such as 80kVA isolation transformer burglar alarm that can effectively protect the outdoor transformers and solve the problem that power workers deal for many years. Burglar alarm device is installed next to transformer or on the telegraph pole. Once a front-end processor detects disconnection and power failure, it will sent GSM message to the four alarm personnel and alarm information to monitoring center, at the same time it will trigger the voice alarm of on-site loudspeaker. The step up and step down transformer that sends out the alarm information and the actual location of faulty line are clearly displayed on the electronic map of monitoring center. After receiving the alarm, the police on duty will immediately be sent to the scene to have a check and deal with the related problem. In addition to disconnection and warning, the machine can access to the alarm amount of vibration, infrared ray, wire wrapping and others for the purpose of protecting the transformer safety.