1-phase/ 3-phase alternating current generator with four pole, rated voltage 220V/ 230V/ 240V/ 380V/ 400V/ 460V can be chosen. AC synchronous generator has an elegant appearance, sturdy and durable structure, convenient maintenance and long service life.
Tips: Normal Maintenace of AC Synchronous Generator.
1. Check whether the grounding wire of direct current generator is good.2. Check the operation status of the exhaust fan in the engine room, and whether the diesel oil is enough to run for eight hours.3. Check whether the cold water level and engine oil level are normal.4. After the manual test machine runs normally, turn on the automatic air switch of the generator, and switch the main switch to the automatic start position, perform a simulated power failure test, and observe the automatic start condition of the generator.5. Run the generator under load for one hour, and observe whether the indicators of the instruments and the unit are operating normally.